view less−Product Description
US Water 2" Flow Backwashing Greensand Plus Filter for up to 64 GPM
Designed to reduce or remove iron, manganese and/or low-levels of sulfur for commercial, industrial and municipal applications.
- Automatic 12-Day Time-Clock Control - Simple to set
- Just one internal moving part
- NSF Certified Fiberglass Resin Tanks
- 2" Full-Flow Hub and Lateral Distributors (shown at right)
- Utilizes Greensand Plus Manganese Dioxide Media
- Perfect for Iron & Sulfur Removal
- Often used with a chlorine feed ahead of the system (continuous regeneration)
- Ideal for RO Pre-Treatment
- Protective NEMA 3R equivalent enclosure is rain tight, and UV stable
|Model Number||Cubic Feet Media||Pounds Gravel||Peak Flow Rate||Backwash Flow Rate||Mineral Tank||Shipping Weight|
|10||250||37 GPM||35 GPM||24 x 72||1350 lbs|
|15||350||55 GPM||55 GPM||30 x 72||1975 lbs|
|20||500||84 GPM||85 GPM||36 x 72||2650 lbs|
view less-Additional Information
|Manufacturer||US Water Systems|
|Select Media Type||GSP – Greensand Plus|
view less-Ratings & Reviews
view less-Product FAQs
I have four wells. #1, 0.0113 (I), 0.0152 (M); #2, 0.0465 (I), 0.0253 (M); #3, 0.0131 (I), 0.0233 (M); #4, 1.06 (I), 0.274 (M). (I=iron, M=manganese) All three wells pump 12 gallons per minute average. 20,000 gpd is typical. Will this unit handle the levels and flow rates? 140-31F-GSP-15
This system would not be a good fit for you. You must have enough flow rate from the well pump to backwash the system. If your well pumps are only capable of 12 GPM, you will need to choose the system that backwashes at the pump flow rate.
You will need (3) three of these if you only have 3 well pumps;
You will need to choose the 10 GPM systems. You will plumb all three of these in parallel and then offset the backwash time for each unit to ensure they are not backwashing at the same time. This is the best way to ensure you have the adequate backwash rate for each unit but still meet the service flow rate you require.
You will need to inject chlorine prior to these filters to get a 0.5-1 ppm residual chlorine level after the filters. This helps with the oxidation process prior to the Greensand Plus filter.
You will need the system below;
You will need chlorine as well;
This will be the typical set up for a Greensand Plus system. I hope this helps.