How Deionization Works
By definition, deionization â€“ often called DI for short â€“ is used in connection to the removal of ions from the water. Deionization is typically accomplished by passing water through two ion exchange columns, one positively charged and one negatively charged. The ions, which have positive or negative charges, are exchanged for H+ ions or OH- ions. The H+ ions react with the OH- ions, leaving no ions remaining in the solution. It's also possible to use a mixed bed of cation (negative) and anion (positive) exchange resins in a DI cartridge, simplifying the process of deionization.
How Deionizer Cartridges Work
To purify water with a DI cartridge system, water that has already been filtered to remove particulate matter (and, in many cases, which has already passed through a reverse osmosis filter) is piped into a standard filter housing. This housing typically contains two or more deionizer cartridges, and may also include additional filters as well. As the water flows into the cartridge, it passes through the mixed bed resin, which attracts nearly all of the mineral ions and replaces them with H+ and OH-. These new ions combine to form H20 â€“ water. You're left with high purity water that can be used for a range of industrial purposes.
In addition to being simpler, it's more cost effective to purify water using DI cartridges in housings or pods. The regeneration process by which the mineral ions that have been removed from the water are cleaned out of the mixed resin beds so that the resin can be reused involves hydrochloric acid and liquid sodium hydroxide, both of which are potentially dangerous and must be disposed of properly. It is more affordable and practical to use a deionizer cartridge system, replacing the cartridges when they are exhausted and sending the old cartridges out to a bulk regeneration plant to have them regenerated and recycled.